Enphase M250 Microinverter- M250-60-2LL-S22 (H4 PV input, 16" Engage Cable out)
For 60 Cell Modules
The Enphase M250 Microinverter delivers increased energy harvest and reduces design and installation complexity with its all-AC approach. With the M250, the DC circuit is isolated and insulated from ground, so no Ground Electrode Conductor (GEC) is required for the microinverter. This further simplifies installation, enhances safet, and saves on labor and materials costs.
The Enphase M250 integrates seamlessly with the Engage Cable, the Envoy Communications GatewayT™, and Enlighten, Enphase’s monitoring and analysis software.
- Optimized for higher-power modules
- Maximizes energy production
- Minimizes impact of shading, dust, and debris
- No GEC needed for microinverter
- No DC design or string calculation required
- Easy installation with Engage Cable
- 4th-generation product
- More than 1 million hours of testing and 3 million units shipped
|Recommended input power (STC)||210 - 300W|
|Maximum input DC voltage||48V|
|Peak power tracking range
||27V – 39V|
|Operating range||16V – 48V|
|Min./Max. start voltage||22V/48V|
|Max. DC short circuit current||15A|
|Max. input current||9.8A|
|@208 Vac||@240 Vac|
|Peak output power||250W||250W|
|Rated (continuous) output power||240W||240W|
|Nominal output current
||1.15A (arms at nominal duration)||1.0A (arms at nominal duration)|
|Nominal frequency/range||60.0/57-61 Hz||60.0/57-61 Hz|
|Extended frequency range*||57-62.5 Hz||57-62.5 Hz|
|Maximum units per 20A branch
||24 (three phase)||16 (single phase)|
|Maximum output fault current||850 mA rms for 6 cycles||850 mA rms for 6 cycles|
|CEC weighted efficiency, 240 VAC
|CEC weighted efficiency, 208 VAC
|Peak inverter efficiency||96.5%|
|Static MPPT efficiency (weighted, reference EN 50530)||99.4%|
|Night time power consumption||65mW max|
|Ambient temperature range||-40ºC to +65ºC|
|Operating temperature range (internal)||-40ºC to +85ºC|
||171 mm x 173 mm x 30 mm (without mounting bracket)
6.73" x 6.81" x 1.18" (without mounting bracket)
|Cooling||Natural Convection – No Fans|
|Enclosure environmental rating||Outdoor – NEMA 6|
|Compatibility||Compatible with 60-cell PV modules.|
||The DC circuit meets the requirements for ungrounded PV arrays in NEC 690.35. Equipment ground is provided in the Engage Cable. No additional GEC or ground is required.|
|Monitoring||Free lifetime monitoring via Enlighten software|
|Compliance||UL1741/IEEE1547, FCC Part 15 Class B
CAN/CSA-C22.2 NO. 0-M91, 0.4-04, and 107.1-01
Enphase Energy Microinverter
25-Year Limited Warranty
Enphase Energy Inc. (“Enphase”) has developed a highly reliable microinverter, designated as M215-60-2LL-S22, M215-60-2LL-S23, M215-60-230-S22 or M215-60-230-S23 (“Microinverter”), that is designed to withstand normal operating conditions when used for its originally intended purpose in compliance with the Enphase User Manual supplied with the originally shipped system. The Enphase limited warranty (“Limited Warranty”) covers defects in workmanship and materials of the Enphase Microinverter (“Defective Product”) for a period of twenty-five (25) years from the date of original purchase of such Microinverter at point of sale to the originally-installed end user location (the “Warranty Period”). During the Warranty Period, the warranty is transferable to a different owner as long as the Microinverter remains installed at the originally-installed end user location.
During the Warranty Period, if Enphase establishes, through inspection, the existence of a defect that is covered by the Limited Warranty, Enphase will at its option, either (1) repair or replace the Defective Product free of charge, or (2) provide a credit or refund to the owner of the system at the originally-installed end user location in an amount not to exceed the then-current price of a “like kind” microinverter(s) that is available for purchase by the system owner at the time of the Limited Warranty claim, or (b) the original cost of the Enphase Microinverter that is subject to a Limited Warranty claim.
If Enphase elects to repair or replace the Defective Product, Enphase will, at its option, use new and/or reconditioned parts in repairing or replacing the Defective Product. Enphase reserves the right to use parts or products of original or improved design in the repair or replacement of Defective Product. If Enphase repairs or replaces a Defective Product, the Limited Warranty continues on the repaired or replacement product for the remainder of the original Warranty Period or ninety (90) days from the date of Enphase’s return shipment of the repaired or replacement product, whichever is later. The Limited Warranty covers both parts and labor necessary to repair the Defective Product (if Enphase elects to repair the Defective Product), but does not include labor costs related to (i) uninstalling the Defective Product or (i) if applicable, re-installing a repaired or replacement product. To the extent applicable, the Limited Warranty also covers the costs of shipping a repaired or replacement product from Enphase, via a non-expedited freight carrier selected by Enphase, to locations within the United States (including Alaska and Hawaii) and Canada, but not to other locations outside the United States or Canada. The Limited Warranty does not cover, and Enphase will not be responsible for, shipping damage or damage caused by mishandling by the freight carrier and any such damage is the responsibility of the freight carrier.
To obtain repair or replacement service, credit or refund (as applicable) under this Limited Warranty, the customer must comply with the following policy and procedure:
1. All Defective Product must be returned with a Return Merchandise Authorization Number (RMA) which customer must request from Enphase. Before requesting the RMA, however, the customer should contact an Enphase technical support representative to evaluate and troubleshoot the problem while the Enphase Microinverter is in the field, since many problems can be solved in the field.
2. If in-field troubleshooting does not solve the problem, Customer may request the RMA number, which request must include the following information:
- Proof-of-purchase of the Defective Product in the form of (1) the dated purchase receipt from the original purchase of the product at point of sale to the end user, or (2) the dated dealer invoice or purchase receipt showing original equipment
manufacturer (OEM) status, or (3) the dated invoice or purchase receipt showing the product exchanged under warranty
- Model number of the Defective Product.
- Serial number of the Defective Product.
- Detailed description of the defect.
- Shipping address for return of the repaired or replacement product (as applicable).
3. All Defective Product authorized for return must be returned in the original shipping container or other packaging that is equally protective of the product.
4. The returned Defective Product must not have been disassembled or modified without the prior written authorization of Enphase.
Enphase Microinverters are designed to withstand normal operating conditions and typical wear and tear when used for their original intent and in compliance with the installation and operating instructions supplied with the original equipment. The Limited Warranty does not apply to, and Enphase will not be responsible for, any defect in or damage to any Enphase Microinverter: (1) that has been misused, neglected, tampered with, altered, or otherwise damaged, either internally or externally; (2) that has been improperly installed, operated, handled or used, including use under conditions for which the product was not designed, use in an unsuitable environment, or use in a manner contrary to the Enphase User Manual or applicable laws or regulations; (3) that has been subjected to fire, water, generalized corrosion, biological infestations, acts of God, or input voltage that creates operating conditions beyond the maximum or minimum limits listed in the Enphase Microinverter specifications, including high input voltage from generators or lightning strikes; (4) that has been subjected to incidental or consequential damage caused by defects of other components of the solar system; or (5) if the original identification markings (including trademark or serial number) of such Microinverter have been defaced, altered, or removed. The Limited Warranty does not cover costs related to the removal, installation or troubleshooting of the customer’s electrical systems. The Limited Warranty does not extend beyond the original cost of the Enphase Microinverter.
THE LIMITED WARRANTY IS THE SOLE AND EXCLUSIVE WARRANTY GIVEN BY ENPHASE AND, WHERE PERMITTED BY LAW, IS MADE EXPRESSLY IN LIEU OF ALL OTHER WARRANTIES, EXPRESS OR IMPLIED, STATUTORY OR OTHERWISE, INCLUDING, WITHOUT LIMITATION, WARRANTIES OF TITLE, QUALITY, MERCHANTABILITY, FITNESS FOR A PARTICULAR PURPOSE OR NON-INFRINGEMENT OR WARRANTIES AS TO THE ACCURACY, SUFFICIENCY OR SUITABILITY OF ANY TECHNICAL OR OTHER INFORMATION PROVIDED IN MANUALS OR OTHER DOCUMENTATION. IN NO EVENT WILL ENPHASE BE LIABLE FOR ANY SPECIAL, DIRECT, INDIRECT, INCIDENTAL OR CONSEQUENTIAL DAMAGES, LOSSES, COSTS OR EXPENSES HOWEVER ARISING, WHETHER IN CONTRACT OR TORT, INCLUDING WITHOUT LIMITATION ANY ECONOMIC LOSSES OF ANY KIND, ANY LOSS OR DAMAGE TO PROPERTY, OR ANY PERSONAL INJURY.
To the extent any implied warranties are required under applicable law to apply to the Enphase Microinverter, such implied warranties shall be limited in duration to the Warranty Period, to the extent permitted by applicable law. Some states and provinces do not allow limitations or exclusions on implied warranties or on the duration of an implied warranty or on the limitation or exclusion of incidental or consequential damages, so the above limitation(s) or exclusion(s) may not apply. This Limited Warranty gives the customer specific legal rights, and the customer may have other rights that may vary from state to state or province to province.